10kV～36kV class single-phase pole-mounted distribution transformer
The transformer is cylinder sealing structure. Each one is fixed with grounding devices, hooks, supporting lugs
which conforms to ANSI standard, and one or two high voltage bushing on the cover, low voltage bushing on the
wall of the tank and eyebolt connecting terminals. The tap changer should be adjusted basing on the instruction
after the power off.
Complete Self Protect type
This type of transformers are CSP type, which can protect itself from thunder and lighting, short circuit and
protect the transiting and distribution line from current failure because of self-malfunction.
Except from some similarities such as cylinder tank, hooks, lifting lugs, grounding devices, nameplates, core
and winding with the conventional type. This type of transformers have characteristics and devices as follows:
One or two high voltage bushings are on the cover with fuse.
One or two arresters are installed on the wall of the tank, whose top end is near to the high voltage bushing, and
connected to the bushing by a copper strip. One secondary breaker switch is above the winding inside the tank,
and here are operating handle, overload reset and signal light.
Low voltage bushing is educed from the wall of the tank, grounding device is fixed to position X2. One end of
the single bushing leads out through the high voltage bushing, the other end is ground connection.
Core: C.R.G.O. core and amorphous metal core can be chosen.
Lighting industry: +86 757 8625 5247
Energy industry +86 757 8625 6819
Industrial control: +86 757 8625 6813
Power industry +86 757 8252 3536
Hotline operator: +86 757 86256888
Copyright © Eaglerise Electric & Electronic (China) Co., Ltd. All Rights Reserved.Technical support: Reanod